Optimization for Biogas Power Plants using Automatic Control of Gas Pressures
In many cases, gas storages on biogas power plants are not used optimally to store gas as much as their capacity. The digester is sometimes overload to store gas and the controller cannot deliver gas to other storage. Consequently, gas is often released from digester to avoid over pressure. At the end, biogas power plant has less efficiency. Hence, a mechanism to control gas pressure to make different pressure between its storages is required. Fans were used to manipulate the most majority system pressures on a biogas power plant using frequency converters. Measurements, simulations, and experiments were conducted to create a new system on a biogas power plant. A controller, Programmable Logic Controller was used to control the entire system pressure using Proportional-Integral-Derivative algorithm. When the gas pressures are not in the allowable range of pressure, then the controller changes the fans’ frequency to the desired conditions. As a result, gas moves to another storage and system pressures are in the allowable range.
Bwe, â€œInternal report bwe,Daten Geigerâ€?, Friesoythe, 2010.
Balasubramania, S, â€œNon linear fermenter with pressure dynamicsâ€?, ME 697Y Intelligent system, Purdue University, 2012.
DIN 4134, Deutsche Norm 4134, “Tragluftbauten: berechnung, ausführung,
und betriebâ€?, Germany, February 1983.
Driscoll, S, â€œThe Design and Qualification of a Hydraulic Hardware-in-the- Loop Simulatorâ€?, School of Mechanical Engineering Georgia Institute of Technology ,August 2005.
Liermann , Dr.-Ing. Matthias, â€œPressure Control using PID and Nonlinear Input/Output Linearization Method Approachâ€?, American University of Beirut.
Sanstede et al .G, US3516429 â€œSystem for automatic control of gas pressureâ€?, June 23, 1970.
Shaw, A. J, â€œThe PID Control Algorithm How it works, how to tune it, and how to use itâ€?, Process Control Solutions, December 1, 2003.
Siemens, â€œSiemens Standard Software for S7-300 and S7-400 PID Control user manual C79000-G7076-C516-01, Siemens AG Automation Group Industrial Automation Systemsâ€?, Germany, 1996.
Vukic, Prof. Zoran, â€œAutomation and Robotics Research Institute The University of Texas at Arlington, LECTURES ON PID CONTROLLERSâ€?, PhD Faculty of Electrical Engineering and Computing University of Zagreb, Ognjen Kuljaca, April 2002.
Vodencarevic, A, â€œDesign of PLC-based Smith Predictor for Controlling Processes with Long Dead Timeâ€?, proceeding IMECS, Hongkong, 2010. crossref
Wolf .C, et all, â€œBiogas Plant Control and Optimization Using Computational Intelligence Methods Biogasanlagenregelung und -optimierung mit Computational Intelligence Methodenâ€?, Cologne University of Applied Sciences, Automatisierungstechnik 57 (2009) 12. crossref
(2012, February). "Oekobit biogas process." [Online]. Available: http://www.oekobit-biogas.com/en/the-biogas-process.html
(2012, February). "Under pressure fan." [Online]. Available: http://www.karl-klein.de/produktuebersicht/niederdruck-ventilatoren/
(2012, March). "Technical support of Siemens PLC." [Online]. Available: http://support.automation.siemens.com
Metrics powered by PLOS ALM
- There are currently no refbacks.